Bagaimana memulai menkonfigurasi PLC Siemens dengan TIA Portal, sebenarnya caranya mirip menggunakan simatic manager
1. Open the PLC Siemens project in the TIA Portal software.
2. Select the PLC from the project tree and open the PLC Properties.
3. In the General tab, select Protection, make sure that Full access (no protection) is selected.
4. Then scroll down the page and check Permit access with PUT/GET communication from remote partner.
NOTE: If variables are defined into “Program blocks”, DB must configured as “Not optimized”.
To check or change DB optimization, enter DB Properties:
Then into General > Attributes uncheck “Optimized block access” as below:
If checkbox “optimized block access” is not available (grayed out) could depends if DB is an “instance DB” linked to an “optimized access FB”.
Now, compiling the project, tags offsets will showed near variable name.